The IR test measurement obtained is intended to indicate the integrity of the electrical insulation, whereas the higher the IR level the better the condition of the insulation. Ideally, an IR test reading should be at an infinite level. However since no insulators are perfect and leakage currents will flow through the dielectric material, between the conductive parts, it ensures that a finite resistance value can be measured. When performing IR testing there are generally three types of current flow detected. It is important to understand all three types of current and how they affect the IR readings: Capacitive charging current is the current that flows upon application of the DC voltage to charge the capacitance between the insulation system under test and earth. This current level will be high in the first instance before dropping off quickly to zero as the capacitor is charged (i.e. within 1 second. Dielectric Absorption current is the polarizing current that is drawn by the insulation system to align the dipoles within the dielectric material, with the applied electric field. This current level is high initially but then gradually drops off as the dipoles in the insulation become increasingly polarized (i.e. on the order of 10 minutes to hours). Leakage current is the resistive current that continuously flows through the insulation to ground via any leakage paths that may exist in the dielectric materials. Obviously, a low leakage current level implies that an insulation system is in good condition. The leakage current level should also stay more or less constant over time in good insulation materials. While it can be useful to monitor all three types of current during IR testing, both the Leakage current and Dielectric Absorption current are the two measurements that are most commonly used in evaluating the insulation’s overall integrity. However, the Capacitive charging current measurement is also a useful indication of the age and performance of the insulation’s dielectric materials. It is very difficult to detect that type of current unless you are using a permanently installed automatic (PIA) IR testing system to test the equipment. That’s because the capacitive charging current causes the IR reading to initially be very low and then it will quickly rise to a higher reading within seconds. This occurrence indicates that the insulation is in good condition and the operating life expectancy is also good. If the IR reading were to drop immediately to a very low level and then not quickly raise up higher, it would indicate that the insulation is aging and the operating life left has been diminished due to defects in the insulation materials. The Dielectric Absorption or Polarization current measurement is time dependent, because the current decreases slowly over time while the DC test voltage is being applied. This type of current measurement is commonly referred to as a Dielectric Absorption Ratio (DAR) or Polarization Index (PI) ratio test. When performing these tests the IR reading is used to create a ratio between a 30 second and a 60 second IR reading for the DAR test, or a one minute and a ten minute IR reading for the P.I. test. A minimum ratio of (1.6) for the DAR test or a minimum ratio of (3) for the PI test indicates that the insulation is in acceptable condition. Any ratio less than these minimum values indicates that there are parallel leakage paths through the insulating materials which indicates that there is a problem. The most common cause of insulation degradation is surface moisture on the dielectric insulation materials. The moisture creates parallel leakage paths to ground through cracks or defects in the insulation materials. These tests are very useful in determining the present “Real Time” electrical condition of the insulation materials. The Leakage current measurement is the most commonly used value to indicate the overall dielectric condition of the insulation, and is the current being measured during an IR test. Leakage current is time and frequency dependent, which means the number of tests performed and the duration of time that the testing is performed affects the testing results. Ideally, the IR test reading should increase slowly over time and then maintain a stable consistent level. This type of test, when done manually, is typically performed as a “spot type” test and is affected by the ambient temperature of the insulation at the time of the test. The IR reading then requires a temperature conversion to obtain the true leakage current at that time. However, with the new style permanently installed automatic (PIA) type of IR testers, the leakage current testing is done continuously over long periods of time. The numerous test results then become averaged over time, resulting in leakage current readings that are therefore temperature independent, meaning these IR readings do not require a temperature correction and the resulting value is the “True” leakage current of the insulation. A low IR leakage current reading that is maintained over a long period of time and does not fluctuate is, in theory, in acceptable condition, even if the IR reading is below the recommended minimum safe level as outlined in IEEE Standard 43-2000. An IR test reading that begins at a high level and then has a significant decrease over time is then considered to be unacceptable and an indication of defects in the insulation. An IR test reading that begins at a low level and then slowly rises to a level greater than four times the initial level, indicates that the insulation is in new or excellent operating condition. The new method of permanently installed automatic (PIA) IR testing is far more accurate and has become a more reliable method of determining the “true” IR leakage current in the insulation.